WhatsApp/WeChat/Skype/Phone：+86 186 2550 3172
The three core cables are designed for distribution of electrical power with nominal voltage Uo/U ranging from 3.6/6.6KV to 19/33KV and frequency 50Hz.
They are suitable for installation mostly in power supply stations, indoors and in cable ducts, outdoors, underground and in water as well as for installation on cable trays for industries, switchboards and power stations.
Plain annealed copper or aluminium complying with IEC 60228/BS 6360. Copper conductors shall be stranded (class 2) and aluminium conductors shall be either solid or stranded (class 2).
Extruded layer of semi-conducting cross-linkable compound is applied over the conductor and shall cover the surface completely. The minimum thickness is 0.3mm and the maximum resistivity shall not exceed 500 Ohm-m at 90°C.
Insulation is of cross-linked polyethylene compound XLPE (GP8) conforming to BS 7655-1.3 or EPR (GP7), conforming to BS 7655-1.2.
Request an OEM or Custom Quote
Let's together work as for your project.
Choice The Voltage
0.6/1kv1.8/3KV3.6/6KV6/10KV10KV11KV15kv8.7/15KV18/30KV33KV26/35KV Or Others:
Choice The Conductor
AluminumCopper Or Others:
Choice The Insulation
XLPEPVCLSZH Or Others:
Choice The Armoured
SWASTAAWAATANon-armoured Or Others:
Choice The Core
1Core2Core3Core4Core5Core Or Other:
Choice The Section Area
6mm210mm216mm225mm235mm250mm270mm295mm2120mm2185mm2240mm2300mm2400mm2500mm2630mm2800mm21000mm2 Or Other:
Starting custom your ideal size, the factory price will send you in 12 hours.
Table 1. Insulation Thickness
Nom. Cross Section Area
Insulation Thickness at Nominal Voltage
70 – 185
Extruded layer of semi-conducting cross-linkable compound is applied over the insulation. The extruded semi-conducting layer shall consist of bonded or cold strippable semi-conducting compound capable of removal for jointing or terminating. As an option, a semi-conducting tape may be applied over the extruded semi-conducting layer as a bedding for the metallic layer. The minimum thickness is 0.3 mm and the maximum resistivity is 500 Ohm-m at 90°C. The screen is tightly fitted to the insulation to exclude all air voids and can be easily hand stripped on site.
Inner Covering & Fillers
For cables with a collective metallic layer or cables with a metallic layer over each individual cores with additional collective metallic layers, semi-conducting inner covering and fillers shall be applied over the laid up cores. The inner covering is made of non hygroscopic material, except if the cable is to be made longitudinally watertight. The inner covering shall be extruded or lapped.
The approximate thickness of extruded inner coverings is given in Table 2:
Ficititous Diameter over Laid Up Cores
Approx. Thickress of Extruded Inner Covering
*The approximate thickness of lapped inner coverings shall be 0.6mm.
The metallic layer shall be applied over each core or applied as a collective screen. The metallic screen shall consist of either copper tapes or a concentric layer of copper wires or a combination of tapes and wires. The metallic layer provides an earth fault current path, capable of withstanding fault current to earth of 1000A for one second at maximum temperature 160°C. Copper wires are applied over the conducting water blocking layer with a minimum diameter of 0.5mm. And over the copper wires, copper tape with minimum thickness of 0.1mm can be applied helically with overlap.
Total cross section of copper wire screen is shown in table 3:
Nominal Cross-Section Area of Cable
Minimum Cross-Section of Copper Wire Screen Area
DC Resistance of the Copper Wire Screen
up to 120
Separation Sheath (for armoured cable)
The separation sheath comprises a layer of extruded PVC, PE or LSZH. The nominal thickness is calculated by 0.02Du + 0.6mm where Du is the fictitious diameter under the sheath in mm. The nominal separation sheath thickness shall not be less than 1.2mm.
Armour (for armoured cable)
The armour consists of galvanized steel wire applied over the inner covering with diameter specified as in Table 4.
Fictitiious Diameter under the Armour
Armour Wire Diameter
Overall sheath comprises a layer of extruded either PVC type 9 conforming to BS 7665-4.2 or MDPE type TS2 conforming to BS 7655-10.1; LSZH can be offered as an option. The over sheath is normally black in colour. When a DC voltage test is to be performed on the over sheath, a semi-conducting layer such as graphite coating shall be applied over the surface of the extruded over sheath. The nominal over sheath thickness is calculated by 0.035+D where D is the diameter immediately under the over sheath in mm. For cables with the over sheath not applied over the armour, the nominal over sheath thickness shall not be less than 1.4mm. And for cables with over sheath applied over the armour, the nominal over sheath thickness shall not be less than 1.8mm.
up to 90°C
-5°C ( PVC or LSZH sheath ); -20°C ( PE sheath )
Short Circuit Temperature
250°C (short circuit duration up to 5 seconds)
15 x OD
Rated Voltage Uo/U
Operating Voltage (Um)
Testing Voltage (rms)
*Describe Your Buying Requirements in Detail